User:PetesGuide/FASTON terminal

FASTON terminal

AMP FASTON terminals are widely used in electronic and electrical equipment, and compatible terminals are manufactured by many different vendors, commonly using the term "quick disconnect" or "tab" terminals. They are similar in size to some of the Packard terminals, such as Packard 56, and may have been derived from them.

Four different series are available, named after their width in inches. . Insulated versions of the terminals are color-coded to indicate what gauges of stranded wire they may be used with. The terminal system consists of tabs (male) and receptacles (female). There are also versions of both tabs and receptacles that can be mounted directly to circuit boards.

A little-known hand tool exists for inserting the terminals, the AMP Universal Handle.

Specifications

 * PIDG FASTON (Nylon) terminals are defined in AMP Specification 114-1002: Terminal, FASTON, PIDG, Application of
 * PLASTI-GRIP (Vinyl) (insulation restricting) terminals are defined in AMP Specification 114-1003: Terminal, FASTON, PLASTI-GRIP, Application of
 * UL 310 “Standard for Electrical Quick--Connect Terminals”
 * CSA 22.2 #153, “Quick--Connect Terminals”
 * UL 486 also specifies the testing of standard wire connectors and soldering lugs.
 * MIL-T-7928
 * http://www.te.com/content/dam/te-com/documents/industrial-automation-and-control/global/1773464-1_QRG_PIDG.pdf

Crimp Styles
Two main styles of crimps are specified by AMP:
 * "F" Crimp for use on non-insulated connectors
 * TETRA-CRIMP for use on insulated PIDG and PLASTI-GRIP connectors
 * "C" Crimp - typically used for flag connectors (where the wire enters the connector perpendicular to the direction of tab insertion)
 * Tab-Lok - typically used for flag connectors

312 Series
0.312 inch male tab width

250 Series
0.250 inch male tab width
 * 10 AWG, 24 amps (continuous)
 * 12 AWG, 20 amps (continuous)
 * 14 AWG, 15 amps (continuous)
 * 16 AWG, 10 amps (continuous)
 * 18 AWG, 7 amps (continuous)
 * 20 AWG, 4 amps (continuous)
 * 22 AWG, 3 amps (continuous)

205 Series
0.205 inch male tab width
 * 14 AWG, 15 amps (continuous)
 * 16 AWG, 10 amps (continuous)
 * 18 AWG, 7 amps (continuous)
 * 20 AWG, 4 amps (continuous)
 * 22 AWG, 3 amps (continuous)

187 Series
0.187 inch male tab width
 * 16 AWG, 10 amps (continuous)
 * 18 AWG, 7 amps (continuous)
 * 20 AWG, 4 amps (continuous)
 * 22 AWG, 3 amps (continuous)

125 Series
0.125 inch male tab width

110 Series
0.110 inch male tab width
 * 16 AWG, 5 amps (continuous)
 * 18 AWG, 4 amps (continuous)
 * 20 AWG, 3 amps (continuous)
 * 22 AWG, 2 amps (continuous)